Check the air filter resistance value.
Check the unit for abnormal vibration, excessive exhaust gas, excessive noise or leakage of coolant and fuel during operation. Regular test runs can lubricate engine components, which can improve starting reliability; prevent oxidation of circuit connections; and consume fuel to prevent deterioration. When the standby unit is running without load, the time can be 10-15 minutes. Trial operation should be performed twice a month.
Check fuel level and transfer pump condition.
Check the exhaust system for leaks or excessive resistance and drain condensate.
Check the connection of the Cummins generator
battery pack in Dongguan
. Charge the battery when the specific gravity of the battery fluid is below 1.26.
Check the ventilation resistance of the air intake of the generator set; check whether the maintenance tools are ready. http://kongtiaoweixiu0.cn/